NOTIFIER’s XP6-R six-relay control module provides anintelligent fire alarm system with six Form-C relays.
The first module is addressed from 01 to 154 while theremaining modules are automatically assigned to the next five higher
addresses. Provisions are included for disabling a maximumof three unused modules. A single isolated set of dry relay contacts isprovided for each module address, which is capable of being wired for either anormally-open or normally-closed operation. The module allows the control panelto switch these contacts on command. No supervision is provided for the controlledcircuit.
Each XP6-R module has panel-controlled green LED indicators.The panel can cause the LEDs to blink, latch on, or latch off.
•Six addressable Form-C relay contacts.
•Removable 12 AWG (3.25 mm²) to 18 AWG (0.9 mm²) pluginterminal blocks.
•Status indicators for each point.
Standby current: 1.45mA (SLC current draw with all addresses used; if some addresses are disabled,the standby current decreases).
Alarm current: 32 mA(assumes all six relays have been switched once and all six LEDs solid ON).
Temperature range: 32°F to 120°F (0°C to 49°C).
Humidity: 10% to 93%noncondensing.
Dimensions: 6.8"(172.72 mm) high x 5.8" (147.32 mm) wide x 1.0" (25.40 mm) deep.
Shipping weight: 1.1lb. (0.499 kg) including packaging.
Mounting options: CHS-6 chassis, BB-25 cabinet, BB-XP cabinet, CAB-3 Series (see DN-3549)cabinet, CAB-4 Series (see DN-6857) cabinet, or EQ Series cabinet.
Wire gauge: 12 AWG(3.25 mm²) to 18 AWG (0.9 mm²).
Maximum SLC wiring resistance: 40 or50 ohms, panel dependent.
Relay current: 30mA/relay pulse (15.6 ms pulse duration), pulse under panel control.
Relay contact ratings: 30 VDC; 70.7 VAC.
•Unused addresses may be disabled.
•Rotary address switches.
•FlashScan® or CLIP operation.
•Mount one or two modules in a BB-XP cabinet (optional).
•Mount up to six modules on a CHS-6 chassis in a CAB-3 Series,CAB-4 Series, EQ Series, or BB-25 cabinet (optional).
•Mounting hardware included.